# Example No. D12 Park Trailer (See 552.47)

A park trailer floor is 40 ft. by 10 ft. and has two small appliance circuits; a 1000-VA, 240-V heater; a 200-VA, 120-V exhaust fan; a 400-VA, 120-V dishwasher; and a 7000-VA electric range.

 Lighting (40 x 10 x 3 VA per ft.2) 1200 VA Small appliance (1500 VA x 2 circuits) 3000 VA Laundry (1500 VA x 1 circuit) 1500 VA Subtotal 5700 VA First 3000 VA at 100% 3000 VA Remainder (5700 VA - 3000 VA = 2700 VA) at 35% 945 VA Total 3945 VA

Amperes per Leg

Leg A

Leg B

Lighting and appliances

16.44

16.44

Heater (1000 VA ÷ 240 V)

4.20

4.20

Fan (200 VA x 125% ÷ 120 V)

2.08

Dishwasher (400 VA ÷ 120 V)

3.3

Range (7000 VA x 0.8 ÷ 240 V)

23.30

23.30

Total amperes per leg

46.02

47.24

Based on the higher current calculated for either leg, a minimum 50-A supply cord would be required.

For SI units, 0.093 m2 = 1 ft2 and 0.3048 m = 1 ft.

Pocket Guide to the National Electrical Code(R), 2005 Edition (8th Edition)
ISBN: 0131480014
EAN: 2147483647
Year: 2004
Pages: 120